Architectural luminaires for general illumination in rough service (vandal-resistant) wall or ceiling-mount applications. Ideal for interior or exterior applications where safety and security are a concern. Certain airborne contaminants can diminish integrity of acrylic. Refer to Acrylic Environmental Compatibility tables for suitable uses.


Construction

Bezel: One-piece, die-cast aluminum, low copper alloy (&lt;1% copper), .125" thick. Secured to housing with stainless steel Torx® T10 set screws (two included).

Finish: Standard finish is textured polyester powder coat.

Housing: One-piece, die-cast aluminum, low copper alloy (&lt;1% copper), post-painted in textured polyester powder coat. For use directly over outlet box or conduit entry (1/2" and 3/4" threaded opening).

Gasket: Polycarbonate: Perimeter lens gasket is one-piece silicone "O" ring. Glass: Perimeter lens gasket is closed-cell silicone. Pad mounting gasket (closed-cell neoprene) seals housing to mounting surface.&nbsp;&nbsp;<br><br><br>Optics

Lens: Translucent white, injection-molded, UV-stabilized polycarbonate, .125" thick. Smooth exterior for easy cleaning. Interior pattern diffuses light for uniform surface illumination. Optional borosilicate glass lens available (.250" thick). Optional starburst pattern polycarbonate and borosilicate glass lens available (.250" thick).

Reflectors: CFL: High-gloss white powder coat finish for maximum light output. HID: Semi-specular aluminum. Lamps positioned for uniform brightness and illumination.&nbsp;&nbsp;<br><br><br>Electrical

Ballast – CFL: Class P, electronic, HPF multi-volt. &lt;10% THD with starting temperature of 0°F. HID: High reactance, HPF, starting temperature -20°F (MH) or -40°F (HPS).

Socket – CFL: High-temperature thermoplastic with lamp retention clip. HID: Medium-base 4KV rated porcelain.

Lamps - LED: 3500K standard (4100K also available). CFL: 35K 4-pin lamp(s) standard. HID: Reduced UV lamp is standard. Lamps included unless L/LP is specificied. Incandescent: Lamps not included.