As versatile as it is efficient, the OLWX2 is designed to replace up to 400W metal halide while saving over 88% in energy costs. It combines multiple mounting options with the latest generation of LEDs for a wall pack luminaire which is a whole lot more. Whether you are mounting it to a recessed junction box, conduit/through wiring, as an uplight, as a downlight, or as a floodlight - the OLWX2 has you covered.
The versatile design of the OLWX2 LED combines a sleek, low-profile wall pack and high-output LEDs to provide an energy efficient, low maintenance LED wall pack suitable for replacing up to 400W metal halide luminaires. Available floodlight mounting accessories convert the OLWX2 LED into a highly efficient floodlight.

OLWX2 LED is ideal for outdoor applications such as building perimeters, loading areas, driveways and sign and building floodlighting.


Construction&nbsp;<br><br>Rugged cast-aluminum housing with dark bronze polyester powder paint for lasting durability. Integral heat sinks optimize thermal management through conductive and convective cooling. LED’s are protected behind a glass lens. Housing is sealed against moisture and environmental contaminants (IP65).&nbsp;<br><br><br>Optics&nbsp;<br><br>High-performance LEDs behind clear glass for maximum light output. Light engines are available in nominal 4000 K and 5000 K configurations. See Lighting Facts label and photometry reports for specific fixture performance.&nbsp;&nbsp;<br><br><br>Electrical&nbsp;<br><br>Light engine consists of four high-efficiency Chip On Board (COB) LED’s with integrated circuit boards mounted directly to housing to maximize heat dissipation and promote long life (L73/100,000 hours at 25°C). Electronic driver has a power factor of &gt;90% and THD &lt;20% and a minimum 2.5kV surge rating. Floodlight mounting accessories include an additional 6kV surge.&nbsp;&nbsp;<br><br><br>Installation&nbsp;<br><br>Easily mounts to recessed junction boxes with included wall mount bracket, or for surface mounting and conduit entry with included junction box that has four 1/2” threaded conduit entry hubs. Floodlight mounting accessories (sold separately) include integral slipfitter and yoke mounting options. Each flood mount accessory comes with a top visor and vandal guard. Luminaire may be wall or ground mounted in downward or upward orientation.&nbsp;&nbsp;<br><br><br>Listings&nbsp;<br><br>UL Listed to U.S. and Canadian safety standards for wet locations. Rated for -40° C minimum ambient. Tested in accordance with IESNA LM-79 and LM-80 standards. DesignLights Consortium® (DLC) qualified product. Not all versions of this product may be DLC qualified. Please check the DLC Qualified Products List at www.designlights.org to confirm which versions are qualified.

Five-year limited warranty. Full warranty terms located at www.AcuityBrands.com/CustomerResources/Terms_and_Conditions.aspx. Note: Actual performance may differ as a result of end-user environment and application. All values are design or typical values, measured under laboratory conditions at 25 °C. Specifications subject to change without notice.