Ideal for applications requiring general-purpose emergency lighting exit sign.&nbsp;&nbsp;<br><br><br><b>Construction</b>&nbsp;<br><br>Die-cast aluminum construction - compact housing. Brushed aluminum faceplate with matte black electrostatic polymeric trim. Clear lacquer finish on brushed face inhibits fingerprints and other surface contaminants. Also available in white housing and face.&nbsp;<br>Fully overlapping light seal prevents light leaks. Universal direction chevron knockouts are concealed and easily removed.&nbsp;<br>Provisions for conduit entry and pendant mounting.&nbsp;<br>U.S. Patent No. 5,739,639. Other patents pending.&nbsp;<br>The typical life of the exit LED lamp is 10years.&nbsp;<br>Universal (top, end or back) mounting. Completely concealed, easily removed mounting knockouts and hole plugs. No exposed hardware. Die-cast aluminum canopy provided. Faceplate accessory kit available for one-face to two-face field conversion.&nbsp;<br>Dual-voltage input capability 120 or 277 VAC. Emergency models provided with test-switch, status indicator and a battery that automatically recharges when normal power is restored.&nbsp;<br>Emergency models provided with maintenance-free, sealed nickel-cadmium battery to provide 90 minutes of emergency power if necessary.