Lighting system for walkways designed for use with LED light sources to ensure high visual comfort.

Bollard installation.

Comprising an optical compartment with IP66 protection rating and bollard to be ordered separately.

Optical compartment and bollard in aluminium alloy with powder paint coating treatment to ensure high resistance to atmospheric agents and UV rays. Plastic closure casing in the rear part of the optical compartment.

Complete with plastic cable gland and output cable 0.5 - 1 m long.

Tempered frosted sodium-calcium safety glass.

Optical compartment mounted on bollard by means of a single torxtype stainless steel screw (safety type).

The bollard itself houses two stainless steel rods secured to the base, ensuring the product has high resistance to impacts.

The bollard is anchored to the ground by means of a galvanized and painted steel mounting base.

The bollard can be secured to the ground/paving using anchoring pads (on paving) or a mounting base and counter-plate with clamps fi nished with Dakromet, ensuring further assurances against corrosion (to be ordered separately).

Walky optical compartment with built-in 220 ÷ 240Vac On-Off or 24Vdc remote power supply.

On-Off, Dali, IP67 power supplies are available for 24Vdc versions to be ordered separately.

Bollards are available with IP66 220 ÷ 240Vac built-in power supply for 24Vdc Walky versions (ø100, 90x90 and 270x90mm).

Protection against over-voltages (220 ÷ 240Vac versions): 2kV in Common Mode (CM), 1kV in Differential Mode (DM).

Ambient operating temperature: Ta -30°C +50°C for 24Vdc versions, Ta -20°C +50°C for 220-240Vac (On-Off) versions.

All external screws used are in A2 stainless steel.