<b>Body:</b> Aluminum.

<b>Finish:</b> Powder coated.

<b>Suspension:</b> Stainless steel cables.

<b>Power cable:<b> Silver braided.

<b>Diffuser:</b> Protruding Lens (2.1mm/0.08").

<b>Drivers:</b> HPF electronic drivers for 120-277V (EU-240V), 0-10V, 1% dimming.


<b>Remote Mounting Of Drivers:</b> Wire Size 18 AWG - Max distance (from canopy to drivers) 9.5', Wire size 16 AWG - Max distance 19.5', Wire size 14 AWG - Max distance 29.5'. Drivers must be accesible after installation. 


<b>Remote Emergency:</b> Emergency option provides a 1.5 hour (3 hours for EU) emergency lighting facility. The remote system includes the inverter module, NiCad batteries and a remote wall/ceiling LED charge indicator and test switch (NA only) Maximum distance between wall/ceiling plate and luminaire is 4.5m/15’. Test switch fits a single gang box (not supplied).

<b>Mechanical:</b> Luminaires mount directly over J box (by others - North America only).

<b>L70 @25oC:</b> > 50,000 hrs.

<b>Delivered Lumens:<b> Delivered lumens & 
LPW based on 3000K (min 80 CRI) for White LEDs only.